Published:2010/8/3 11:01:43 |
Power electronic transformer PET (Power-Electronic Transformer) as a new type of power transformers, domestic and foreign researchers have been more and more attention. It is a power electronic converter and contains high-frequency transformer to achieve magnetic coupling through the transformer device. PET at the completion of conventional transformer, isolation and transmission of energy that can play the role of power quality controller is a versatile new transformer. Distribution system can be used to achieve blood pressure but also to ensure power quality.
Two or several sets of parallel operation of PET is an important operation mode transformer has important research value. However, PET studies at home and abroad to focus on its topological structure and control strategy, its application in power system and its operational characteristics of relatively weak. Using master-slave control programs to address the parallel exchange side of the PET output Parallel flow; on PET load occurred in parallel with nonlinear load step changes and the dynamic process of a simulation study. In this paper, parallel distribution with load distribution control strategy PET study, the dynamic simulation of typical operation.
1 PET's basic structure and control strategy
The basic topology of PET into AC - AC - AC converters and AC - DC - AC - DC - AC DC converter double. The former is simple, but the controllability is not high: the latter complex structure, improve the control strategy, applied widely. Typical AC - DC - AC - DC - AC DC dual topology shown in Figure 1.
PET the primary voltage type PWM rectifier with decoupling of the voltage and current double closed loop control, regardless of perceptual load on transformers or capacitive, as long as a certain range, can make the grid power factor close to 1; of the original edges single-phase inverter circuit to achieve high-frequency inverter, you can use open loop control. In order to reduce the size and weight of transformers, transformer using ferrite magnetic materials, high permeability cores. Transformer secondary side rectifier circuit for high frequency rectification, on the distribution transformers are not considered two-way flow of energy, so its use is not controlled rectifier circuit. The output constant pressure, constant frequency AC voltage, PET Vice side inverter circuit voltage closed-loop control.
2 PET parallel operation control principle
Two or several sets of parallel operation of PET is to improve the system reliability and an effective way to expand capacity, the parallel operation of PET is still not deep enough. Vice-side PET and US inverter working principle of the inverter line, while the parallel operation of multiple UPS's achievements rich [5-7], in the PET study can draw the parallel issues.
PET currently proposed parallel control methods include: centralized control, master-slave control mode, logic control and the distribution of non-control mode interconnects . In this paper, for the two interconnection lines of the PET without the parallel operation issues. Figure 2 is a diagram of two PET parallel system, the original parties connected to the same public bus.
In order to avoid parallel transformer loop appears, the station's secondary voltage PET frequency, amplitude and phase to be consistent; for the realization of transformers in parallel between the active load and reactive load stable distribution, the units should have the active tone difference PET the mobility characteristics and reactive properties. PET has the characteristics of the mobility edge inverter control vice diagram shown in Figure 3.
PET secondary voltage of frequency, amplitude and phase depends on the PWM inverter sine pulse modulation signal, sinusoidal modulation characteristics and frequency for a given value of f0, the phase and amplitude of a given value ρ0 the given value. F0 = 50Hz taken to ensure the rated frequency. ρ0 P0 corresponds to the active load of the voltage when the first phase (usually taken as 0, the introduction of active compensation coefficient Kp> 0), the mobility features can form active
ρ = ρ0-KpP (1)
U0 corresponds to the reactive load Q = 0 when the voltage amplitude, the introduction of reactive power compensation factor KQ> 0, can form a poor characteristic reactive power transfer
U = U0-KQQ (2)
On the parallel operation of the PET, ρ0 and U0's value should be the same, the introduction of active and reactive power compensation, when the load changes, the parallel operation of the PET will automatically adjust its output voltage phase angle and amplitude between the transformer automatically distribution of power and stability; to a reasonable size distribution transformer capacity by the load capacity of the PET to its own benchmark of Kp and KQ-unit value should be equal, and generally the 0.01 ~ 0.05.
Poor use of frequency modulation characteristics of PET and the parallel inverter's active power distribution. Clearly, in this control mode, the frequency of different load power supply can not keep to 50Hz; and if the frequency in order to ensure the quality, frequency modulation deviation coefficient values must be very small, this does not help stability and distribution of PET in parallel between the power load. With different initial phase angle of this paper, the mobility features, you can maintain a constant frequency power supply, can be chosen at a reasonable coefficient of the mobility, stability and achieve a reasonable distribution of active load. Involved in parallel the output voltage of the PET are equal to 50Hz frequency must be to ensure normal operation. In Figure 3, because of the frequency of use of closed-loop PI control, can do this.
PET parallel operation may not be exactly the same parameters, the most common is the limiting reactors or cable inductance parameters are different. Figure 3, the voltage measurement point of deliberately set in a public bus, even for the PET parameters of inconsistency, it can guarantee stable power between parallel PET reasonable distribution. If voltage measurement point in the PET output, it can not guarantee this.
In this paper, Matlab6.5/Simulink built a simulation model of two parallel operation with the parameters of PET was simulated. System main parameters: PET rated capacity of 10kVA, rated voltage 240/110V; PET2 rated capacity of 10kVA, system frequency rated voltage 240/110V 50Hz, high frequency transformer frequency 1000Hz, IGBT switching frequency 9000Hz; KP, KQ selenium values were obtained per unit .01, the frequency for a given value of f0 obtained 50Hz, phase ρ0 given value of 0, the amplitude for a given take-unit value is 1.0 U0.
3.1 PET also throw in two parallel operation (case 1)
1.0s, the two PET in low-pressure side of the no-load input from the parallel operation, assume the power factor of 0.8 in the integrated load. The variable waveform shown in Figure 4 - Figure 6. Can be seen from the diagram, two PET waveform corresponding to the same variable. After the parallel operation of the load current equal to the commitment to achieve the current sharing control, and active and reactive load stability and distribution, and frequency to maintain the same constant value.
3.2 PET2 join the parallel operation (case 2)
PET1 with a set run, 1.0s from the empty state when the PET2 input, parallel operation of two PET. The waveform shown in Figure 7 and Figure 8 below. The figure shows, PET1 single run by the state to switch to the parallel operation of the state, its commitment to the load current, active and reactive loads are decreased, down in part by the PET2 to bear, finally achieved between two parallel current sharing PET control and active power, reactive power load distribution and stability of good dynamic response.
This article is based active and reactive characteristics of the mobility equation established PET control strategy and model, based on the model of the dynamic process of parallel operation PET simulation. Simulation results show that the control strategy can be maintained under the premise of the rated power supply frequency, to achieve active and reactive load distribution and stability, and good dynamic characteristics.
Source: Network reproduced
Polaris Technology Contributors Hotline :010-85759704 QQ: 1290347351 Email:
Categories Content feedback mail to a friend Add to Favorites Print "Parallel Operation of Power Electronic Transformer Matlab simulation of the dynamic" of the relevant article
* Parallel operation of power electronic transformer dynamic Matlab simulation (2010-06-18, read 0 times) · DSP In-line UPS uninterruptible power supply control system (2010-06-18, read 0 times) * simplify optical networking a new generation of serial optical converters (2010-06-17, read 5 times) * Embedded Systems in Power Transformer Monitoring (2010-06-10, read 21 times) * large thermal power generating units of thermal process automation solutions ( 2010-06-09, read 1429 times) * Smart power features (2010-06-07, read 43 times) * Virtual Power Plant DCS simulation system (2010-06-03, read 217 times) * Steam Turbine DEH System DEH (2010-06-03, read 591 times) * Low-voltage circuit breaker controller design (2010-06-01, read 999 times) the actual temperature * High Voltage Switchgear Cause Analysis (2010-06-01, Hits 173 times Author: Anonymous) "parallel operation of power electronic transformer Matlab simulation of the dynamic" of the news
* High-voltage transformer short-circuit caused by flaming (2010-06-18, read 1 times) * Huaneng thermal power plant generator transformer Tender Notice (2010-06-18, read 7 times) * 330 kV power grid voltage directly into low voltage ( 2010-06-17, read 27 times) * maximum internal voltage converter transformer for success (2010-06-17, read 1 times) * Three Gorges Project in China for all of the localized current transformers (2010-06-13, read 6 times) * China's first 330kV class transformer capacity of the largest successful exports (2010-06-13, read 3 times) * Nanjing to build the "China first" Smart Grid software base (2010-06-13, read 90 times) * Server consolidation is the first entry point for the power of information (2010-06-13, read 22 times) * power generation industry and the growth of information technology breakthroughs in the critical point of the upcoming (2010-06-13, read 65 times) * 14th Session Soft Fair Awards Announced: Far-ray software monopoly of the two awards (2010-06-12, read 110 times) Hot topics and current transformer relay CFB generator reactive power compensation circuit breaker surge arrester low-carbon converter substation ERP boiler turbine wet FGD solar transmission line relay transformer dynamic TI smart grid technology solutions to achieve a breakthrough 06/18 * accelerate solar photovoltaic industry in Shaanxi province to seize the technological development of high ground 06/17 * New power equipment condition monitoring Application of Technology in Beijing 06/17 * 06/17 · Multitest live test of knowledge for the introduction of MEMS pressure sensor solutions, 06/17 · Ferro investment in PV technology in Asia 06/13 * 102 to complete the world's largest aerospace power tunnel group orientation measurements 06/13 * Shaanxi Power "two rules" technical support system acceptance is completed 06/13 * Electrical Research Institute jointly held with XJ Electric smart grid technology exchange 06/13 * lignite power generation use technology breakthrough 06 / 12 "Transformer" Hot article parallel operation of power electronic transformer dynamic Matlab simulation (0) * Power Transformer Fault components and Prevention (14) * amorphous alloy transformer and Energy Saving (12) * on the transformer Room ventilation of (29) * transformer load tap Field Improvement in power system applications (23) * 3 way rotary transformer / digital converter module interface circuit (13) * transformer protection configuration of ( 53) * Embedded System in Power Transformer Monitoring (21) * flyback transformer switching power supply EMC Design (18) * use of solar PV projects transformerless inverter cable construction (20 ) "Power Electronics" hot paper parallel operation of power electronic transformer dynamic Matlab simulation (0) * Chinese and from high voltage power electronics soft-start technology (787 times) * Power Electronic Systems in Power System with wind Prospect (1064 times) * Power Electronic Systems in the wind energy application and Prospect (1197 times) * of power electronics in the rectifier circuit (834 times) * Power Electronics in Power Systems (1778 times ) * inverter status and future technology development (786 times) * China's new progress in power electronic technology (945 times) * Power Electronics and its applications Ten Years (1392 times) * Power Electronics magnetic components New Development (648 times) News Community Ranking Ranking Ranking Recruitment
University ranked the world's major nuclear power accident inventory of smart grid planning the first to read details Taishan nuclear power equipment industry focus to attract a large number of French customers to develop intelligent electricity grid software in emerging markets stock of the world's top ten terrorist nuclear leak Nanjing Datang Power Transmission Unit 1 back A successful energy saving power industry into the fast lane JETCO Zhuhai, China Huaneng, Guangdong Ming Yang tripartite scenery storage integrated CLP confirmed a minor Daya Bay Nuclear leak but not China Resources Power (Hezhou) Limited Jipin Information Resources Power Inner Mongolia 5 Housing coal development headquarters recruiting Technical and Economic Research Institute China Datang Group, Datang International Dam Career Ningxia Power Generation Co. Ltd. plant recruitment recruitment Company Luneng Baoqing China Resources Power Holdings (Ning) Ltd. Ji Pin Power Plant Talent (Jiangsu Branch Career Datang Power Co. Ltd. in 2010 in Fuyang China Resources China Resources thrall to power job Ji Zhao limited liability company in 2010 Ji Pin Tong Village in Guizhou China Huadian Power Company Limited in 2010 Career Simulator and online collection Simulation of the small collection of novice navigation software posts - Download the attached information in this forum graphic tutorial [Share] Power Marketing Management Information System specification [elaborate] 220kV 240MVA Power Transformer hanging hood overhaul plan group, asked for About Electric Board's view of the turbine power plant to find center edition "Call for Love" · SW2 circuit breaker operating mechanism transformation program 600mw Unit Milling paper Electrical Engineering Society of China, TECHNOLOGY _2007 (0-15 all To extract)
Polaris to set platform papers
Polaris paper for the information to make better, more whole, more accurate, more precise, for the majority of user information to find a more convenient, the North Star opening of this user interaction management platform, hope that everyone actively involved, our managers will receive information first time to deal with!
Change Category: Technology classification type thermal power equipment, electrical safety, electrical fuel technology thermal power plant automation instrument operation and maintenance of chemical substation grid dispatching and communications relay information hydroelectric power nuclear power and new energy electric power electricity energy saving construction of power electronic industry control instrumentation article category classification of other attributes typical application of regulations and professional papers commonly used in information solutions for the exchange of experience Company Articles
Change Keywords: (use between different keywords, "" separated) TBA820M is the number for products that is related with integrated circuit.